Instruction/ maintenance manual of the product G9T White Rodgers
Go to page of 12
035-19592-001 Rev. C (0204) USER’S INFORMA TION, MAINTENANCE AND SER VICE MANU AL MODELS: P*UR / G9T -UP / FG9-UP (Upflow) EFFICIENCY RATING CERTIFIED This product was manufactured in a plant whose quality system is certified/registered as being in conformity with ISO 9001.
035-19592-001 Rev. C (0204 ) 2 Unitary Products Group 7. NEVER . . .S tore flammable materials of any kind near your fur- nace. Gasoline, solvents, and ot her volatile liquids should be stored only in approved containers outside your home. These materials vaporiz e easily and are extremely dangerous.
035-19592-001 Rev. C (0204) Unitary Products Group 3 HOW Y OUR GAS FURN ACE WORKS Y o ur furnace is a very easy appliance to take for granted. Season after season, it sits there in your home, keeping you warm and comfortable. For this reason, you may neve r have given much thought to the way your furnace operates.
035-19592-001 Rev. C (0204 ) 4 Unitary Products Group FURNACE USER MAINTENANCE Every time the filters are changed the following items should be visually inspected: • Check combustion air and vent pipe for blockage or leakage. • Check all components to be sure they are in good condition and that there are no obvious signs of deterioration.
035-19592-001 Rev. C (0204) Unitary Products Group 5 How to Clean your Filter High-velocity filters may be cleaned with a vacuum cle aner or washed with a garden hose. Be sure to shake off excess water and allow f ilter to completely dry before re-installing the filter .
035-19592-001 Rev. C (0204 ) 6 Unitary Products Group If the flame is not detected within 2 seconds of the gas valve opening, the gas valve is shut off and a retry op eration begins. If the flame is lost for 2 seconds during the 10-second stabilization period , the gas valve is shut off and a retry ope ration begins.
035-19592-001 Rev. C (0204) Unitary Products Group 7 CONTINUOUS FLASH: This indicates that flame was sensed when there was not a call for heat. With th is fault code the control will tur n on both the inducer motor and supply ai r blower . A gas valve that le aks through or is slow closing w ould typically cause this fault.
035-19592-001 Rev. C (0204 ) 8 Unitary Products Group SECTION III: REPLACEMENT P ARTS LIST C G R W Y HUM EAC XFMR LINE CIR HUM EAC XFMR LINE PARK PARK HEAT COOL 17 18 23 24 30 25 31 32 33 48 20 21 22 .
035-19592-001 Rev. C (0204) Unitary Products Group 9 ITEM DESCRIPTION MOTOR 1M O T O R , DIRECT DRIV E BLOW ER 2 MOTOR,VENT OR ASS’Y ELECTRICAL 3 CAP ACITOR (7.
035-19592-001 Rev. C (0204 ) 10 Unitary Products Group FIELD INST ALLED A CCESSORIES - NON-ELECTRICAL FIELD INST ALLED A CCESSORIES - ELECTRIC AL MODEL NO.
035-19592-001 Rev. C (0204) Unitary Products Group 11 SECTION IV: WIRING DIAGRAM FIGURE 9: Wiring Diagram.
Subject to change without notice. Printed in U.S.A. 035-19592-001 Rev. C (0204) Copyright © by York International Corp. 2004. All rights reserved. Supersedes: 035-19592-001 Re v.
An important point after buying a device White Rodgers G9T (or even before the purchase) is to read its user manual. We should do this for several simple reasons:
If you have not bought White Rodgers G9T yet, this is a good time to familiarize yourself with the basic data on the product. First of all view first pages of the manual, you can find above. You should find there the most important technical data White Rodgers G9T - thus you can check whether the hardware meets your expectations. When delving into next pages of the user manual, White Rodgers G9T you will learn all the available features of the product, as well as information on its operation. The information that you get White Rodgers G9T will certainly help you make a decision on the purchase.
If you already are a holder of White Rodgers G9T, but have not read the manual yet, you should do it for the reasons described above. You will learn then if you properly used the available features, and whether you have not made any mistakes, which can shorten the lifetime White Rodgers G9T.
However, one of the most important roles played by the user manual is to help in solving problems with White Rodgers G9T. Almost always you will find there Troubleshooting, which are the most frequently occurring failures and malfunctions of the device White Rodgers G9T along with tips on how to solve them. Even if you fail to solve the problem, the manual will show you a further procedure – contact to the customer service center or the nearest service center