Instruction/ maintenance manual of the product 5797A-MT 3M
Go to page of 12
Cold Shrink QS-III Three-Conductor Splice Kit for use on Armor and Non-Armor Cables Instructions IEEE Std. 404 35 kV Class 250 kV BIL * Splices (including size transitions) can be made to smaller or larger conductors , provided both cables are within the Insulation O .
2 78-8126-0432-6-A Contents 1.0 Kit Contents ............................................................................................................................................3 2.0 Prepare Cable ..............................................
3 78-8126-0432-6-A 1.0 Kit Contents: 1.1 Kit Contents are as follo ws: 3 ..............Cold Shrink 5467A QS-III Silicone Splice Bodies 6 ..............T ubes, P55/R Red Compound 3 ..............Metallic Shield Sleeves 6 ..............Constant Force Spring Shield Connectors (1.
4 78-8126-0432-6-A 2.3 Cut the phase cores to the appropriate length. Cores of Cable X should be 33" (838 mm) when measured from the cable jacket end or 31 1/2" (800 mm) when measured from end of the armor .
5 78-8126-0432-6-A 3.0 Place Components on Cable 3.1 Slide one large cold shrink jack et tube onto Cable X and one onto Cable Y with the loose core ribbon ends going on the cable last, extending to ward the cable ends.
6 78-8126-0432-6-A 4.0 Install Splice 4.1 Install connectors. See T able on front cov er of this instruction for proper connector dimensions. Crimp connectors per recommendations from connector manufacturer . For standard 3M ™ connectors, refer to the table at the end of this instruction for crimping information.
7 78-8126-0432-6-A 4.5 Apply red compund on cable insulation, making certain to fill in edges of cable semi-cons. Note: DO NO T use silicone grease. 4.6 Position each splice body ov er the connector and align the leading end of the rubber part with the center of the marker tape.
8 78-8126-0432-6-A 5.0 Install Armor Continuity (If Cable is Armored) 4.10 Unfold the cable f illers and reestablish their lay between the cable phase cores. Hold the fillers in place with a band of 33+ vinyl tape. 4.9 Connect the ground wire(s) from Cable X to the ground wire(s) from Cable Y .
9 78-8126-0432-6-A 6.0 Install Splice Jack et 6.1 Over wrap the e xposed conductors on each side of splice bodies with jacket pieces sa ved from step 2.1. Bind the cable jacket pieces in place with one half-lapped layer of Scotch ™ 88, 1 1/2" wide tape.
10 78-8126-0432-6-A 88 vinyl tape Armorcast ™ wrap 2229 mastic tape 6.5 Apply two half-lapped layers of 4" wide 2229 tape ov er applied vinyl tape in splice center . Overlap ends of Cold Shrink jacket tubes 2" (51 mm). 6.6 Cov er the applied 2229 mastic with two half lapped layers of 88 tape.
11 78-8126-0432-6-A ™ M 3 r o t c e n n o C r e b m u N r o t c u d n o C e z i S r o G W A ( ) l i m c k y d n r u Bp r o C s t t e B & s a m o h T .
IMPORT ANT NOTICE Before using this product, y ou must e v aluate it and determine if it is suitable for y our intended application. Y ou assume all ri sks and liability associated with such use. W arranty; Limited Remedy; Limited Liability . This product will be free from defects in material and manuf acture as of the date of purchase.
An important point after buying a device 3M 5797A-MT (or even before the purchase) is to read its user manual. We should do this for several simple reasons:
If you have not bought 3M 5797A-MT yet, this is a good time to familiarize yourself with the basic data on the product. First of all view first pages of the manual, you can find above. You should find there the most important technical data 3M 5797A-MT - thus you can check whether the hardware meets your expectations. When delving into next pages of the user manual, 3M 5797A-MT you will learn all the available features of the product, as well as information on its operation. The information that you get 3M 5797A-MT will certainly help you make a decision on the purchase.
If you already are a holder of 3M 5797A-MT, but have not read the manual yet, you should do it for the reasons described above. You will learn then if you properly used the available features, and whether you have not made any mistakes, which can shorten the lifetime 3M 5797A-MT.
However, one of the most important roles played by the user manual is to help in solving problems with 3M 5797A-MT. Almost always you will find there Troubleshooting, which are the most frequently occurring failures and malfunctions of the device 3M 5797A-MT along with tips on how to solve them. Even if you fail to solve the problem, the manual will show you a further procedure – contact to the customer service center or the nearest service center